This is an obsolete product, no longer available for purchase.
The DSE548 is an LED expansionmodule for the DSE52xx, DSE53xx and the DSEPower® Series.
The module has been designed to display a maximumof eight local or remote (max 50metres)
individual LED indications.
The DSE548 is presented in a vertical enclosure.
The LED’s are configured using the host module and the appropriate PC software interface.
The LED’s can be configured to be either:
• Extinguish on command
• Light on command
An additional LED indicates that a DC power supply is being received. There is also a flashing ‘Link Lost’ LED fitted to indicate any communication problems with the host module.
When using two expansion modules together each module should be identified as either ‘A’ or ‘B’. This is done by positioning the selector switch on the rear of each module.
• Eight configurable LEDs
• Works up to 50 meters from the host module
• Two modules can be linked together to provide 16 LED indicators
• Interconnecting FCC 68 cable for quick installation
CONTINUOUS VOLTAGE RATING
8V and 35V continuous.
Powered from the plant battery or from a low voltage supply It is able to survive 0V for 50ms during cranking, providing supply was at least 10V before dropout and recovers to 5V. This is achieved
without the need for internal batteries.
MAXIMUM OPERATING CURRENT
20mA @ 12V, 26mA @ 24V
MAXIMUM STANDBY CURRENT
107mA @ 12V, 113mA @ 24V
A OR B MODE SELECTOR
Recessed Jumper Selector on rear
Power On LED
Link Lost (to controller) LED Flashing
8 Configurable LED’s
The module will automatically respond to signals from the host module. The module must be
configured via the host module and a PC. The Expansion LED’s are numbered from 1 to 8 and
appear on the output configuration menu.
144mm x 72mm x 59mm
5.7” x 2.8” x 2.3”
DIN rail mounted housing
138.5mm x 68mm
5.5” x 2.7”
BS EN 61000-6-2
EMC Generic Immunity Standard for
the Industrial Environment
BS EN 61000-6-4
EMC Generic Emission Standard for the Industrial Environment
BS EN 60950
Safety of Information Technology Equipment, including Electrical Business Equipment
BS EN 60068-2-1
Ab/Ae Cold Test -30 °C
BS EN 60068-2-2
Bb/Be Dry Heat +70 °C
BS EN 60068-2-6
Ten sweeps in each of three major axes
5 Hz to 8 Hz @ +/-7.5 mm,
8 Hz to 500 Hz @ 2 gn
BS EN 60068-2-30
Db Damp Heat Cyclic 20/55 °C
@ 95% RH 48 Hours
BS EN 60068-2-78
Cab Damp Heat Static 40 °C
@ 93% RH 48 Hours
BS EN 60068-2-7
Three shocks in each of three major axes
15 gn in 11 mS
DEGREES OF PROTECTION
PROVIDED BY ENCLOSURES
BS EN 60529
IP65 - Front of module when installed into the control panel with the supplied sealing gasket.